Same Business Day Shipping On Most Orders! We are located in Louisville, KY. 40291. In Business Since 1988! Contact Us Anytime if you have questions, need assistance or would like us to look up parts Support@arnoldservice.com We Would Love to fill Your Order, Help You Out and Earn Your Business!
We have many people ask us how do I wire up my new heat pump thermostat? How do I troubleshoot my heat pump thermostat? What do the wire colors mean? What are the functions of the wire and colors? What do the terminals on the thermostat mean? How do I wire up the auxiliary and emergency heat? Below we have an excellent Youtube video Made by AC Service Tech that answers all these questions. If you have any questions please email us anytime. Our email address email@example.com
Question: We have many people ask us the questions: How do I use and read a refrigerant gauge set? How do I check the AC refrigerant level? What do all those numbers and different colors mean? How do I check to make sure I have the right amount of refrigerant in my air conditioner or heat pump system?
Answer: We have three really good Youtube Videos made by Word of Advice TV and AC Service Tech LLC that shows how to read a refrigerant gauge set and how to charge air conditioning systems that use both R410A and R22 refrigerants. I hope this helps you understand how to read a gauge set. I hope these videos help you get your air conditioner or heat pump charged correctly. If you have any questions please email us anytime. Our email address is firstname.lastname@example.org.
My friend, Craig Migliaccio just finished this great book on Refrigerant Charging and Service Procedures for Air Conditioning. If you would like to see more information on the book or purchase here is the link https://www.acservicetech.com/the-book Mr. Migliaccio has dedicated many hours to this excellent book and has been kind enough to make hundreds of Youtube repair and troubleshooting videos. We feature many of these videos taken from the AC Service Tech Youtube Channel on our site! “This book is dedicated to those who are eager to learn the HVACR Trade and Refrigerant Charging/Troubleshooting Practices. In this book, you will find step by step procedures for preparing an air conditioning and heat pump system for refrigerant, reading the manifold gauge set, measuring the refrigerant charge level, and troubleshooting problems with the system’s refrigerant flow. This book differs from others as it gives key insights into each procedure along with tool use from a technician’s perspective, in language that the technician can understand. The book also explains the refrigeration cycle of air conditioners and heat pumps, refrigerant properties, heat transfer, the components included in the system, the roles of each component, airflow requirements, and common problems.”
Procedures Included are:
Vacuum and Standing Vacuum Test
Recovery and Recovery Bottle use
Refrigerant Manifold Gauge Set and Hose Connection and Disconnection
Service Valve Positions and Port Access
Preparation of the System for Refrigerant
Refrigerant Charging and Recovery on an Active System
Troubleshooting the Refrigeration Charge and System Operation.
We have been getting lots of questions about how to install thermostats properly. Many questions are about why my newly installed thermostat is not working properly. I found this excellent Youtube video from AC Service Tech that shows what the top 12 problems and mistakes are when installing or replacing thermostats. I hope this helps you when installing or replacing a thermostat. Thanks so much to AC Service Tech for making this excellent video! Wewould love to help you out and earn your business! Please email us anytime if you have questions. Support@arnoldservice.com
Problem: My air conditioner will not turn on. What could be the problem with my AC not turning on?
Answer: I found this excellent YouTube video from Word of Advice TV that explains many problems that can cause your Air Conditioner to not work or come on. This is one of the best videos I have ever seen on troubleshooting an air conditioner. I hope this helps you find and fix your air conditioner or heat pump system. If you have any questions please respond in the comments below or email me Steve Arnold at: Support@arnoldservice.com. Thanks so much for giving us the opportunity to serve you! Hope you have a blessed day! Steve
Many people have trouble troubleshooting and finding out what is wrong with their air conditioner when it does not work. I found this excellent Youtube video from Word of Advice TV that shows what are the top 10 air conditioner service call problems. I have the video below. I have the problems listed below the video. You can see that many of these problems can be easily fixed and are easy inexpensive problems. I counted 17 top problems and 9 honorable mention problems. I hope this helps you find and fix your air conditioner’s problem. We would love to help you out and earn your business. Please email us anytime if you have questions. Support@arnoldservice.com
Compressor shorted to ground. (will need a new compressor).
Dirty furnace filter
Tripped AC Breaker (If your AC is not coming on I would suggest turning the breaker completely off and back on again to make sure the breaker is on. Do not touch anything metal on your circuit breaker box for safety).
We have this questions asked many times over the years and I want to post my response to this frequently asked question: I am so sorry to hear that you have spent all this money and still do not have a furnace and air conditioner that are working properly! I have this problem asked many times over the years and my answer is: I would strongly recommend that you have your HVAC contractor do a Manual J Heat Gain and Heat Loss calculation on your home before installing a new furnace or doing any other work. We are required here in Louisville, KY to submit a Manual J calculation to the Housing Department, Code enforcement before a permit will be issued to start a new installation. Without the Manual J calculation, it would be a guess as to what size equipment needs to be installed and this is why many people get the wrong size equipment. Requiring a heat gain, heat loss calculation protects the homeowner from getting the wrong size HVAC equipment installed. Most companies have a Manual J computer program where they enter the required information like the home’s orientation (facing north, south, etc.) the amount of insulation, window types, door types and all surfaces that gain or lose heat and more. The computer program will figure the amount of heat loss and gain and tell the contractor what size HVAC equipment needs to be installed. I would recommend that you get this Manual J calculation completed for your home so you know for sure that you are getting the right sized HVAC equipment installed. Even though it is a pain and extra expense for the homeowner and contractor this insures the right size equipment is installed and is invaluable for protecting your energy bill and comfort. We have many other air conditioning and heat pump troubleshooting pages. Please click here to see more troubleshooting advice. Please click here to see the many name brand air conditioner and heat pump repair parts that we sell. We would love to answer your questions and earn your business! If you have any questions please email us anytime: Support@arnoldservice.com
Problem: We have many people ask, “Why is my fan blower motor running all the time. My blower motor will not shut off?” “Why does my fan motor run continuously when I use my furnace?”
Answer: I found a real good Youtube video made by ACServicetech that explains 4 reasons why fan blower motors run continuously. In this video ACServicetech goes over why the Blower Fan Motor Won’t Shut off/Continuously Runs and some of the most common reasons why furnaces or air handlers have this problem. ACServicetech shows step by step Troubleshooting on how to figure out what is causing this problem. This is a great video that I would highly recommend that you watch if your fan motor is running continuously. Many thanks to ACServicetech for making this informative video! If you have any questions please feel free to email us anytime or respond in the comments section below. We have many heating and air conditioning troubleshooting links, Videos and Resources on the following page: Please click here for more troubleshooting resources. We would love to help you out and earn your business! Our email address is: email@example.com
Questions: We have many people ask, “how can I find out why my fan blower motor is not working?” “Why does my fan motor not work when I turn on my furnace or air conditioner?”
Answer: I found a real good Youtube video made by ACServicetech that explains the top 10 reasons why fan blower motors will not come on. ACServicetech goes over what to look for in the system, components that fail most often, how to test the components, where to take readings with a multimeter as well as other tips! This is a great video that I would highly recommend that you watch if your fan blower will not come on. Many thanks to ACServicetech for making this informative video! If you have any questions please email us anytime. Our email address is: firstname.lastname@example.org. We would love to help you out and earn your business!
Question: In May I started to have some problems with my outside ac unit. My fan stopped running but I could get it back running by spinning the blade when it hmmmmmed. Blade was easy to spin Called an AC Company to see what was wrong They said the fan motor was bad and put in a new fan motor and oval capacitor. But didn’t replace the dual capacitor said it didn’t need to be replace it was good. Ran good and cooled down the house good for about a mouth or so but started having the same problems. My fan stop running I could get it back running by spinning the blade when it hmmmmmed. Blade was easy to spin, but motor was hot to the touch Ac company came out again said it was a bad new motor. Company put in a new fan motor and oval capacitor but didn’t replace the dual capacitor said it didn’t need to be replaced that the capacitor was good. Ran good and cooled down the house good for about a mouth or so but started having the same problems. My fan stopped running but it’s hard to spin now and takes a couple of tries to spin when it hmmmmms. The motor was hot to the touch. Now the fan motor won’t start to spin by me spinning it at all. It is too hard to spin. Note: The motor is still hot to the touch. What could be possible wrong with my unit? Why does my fan motor keep burning up?
Answer: Hi! I am so sorry to hear that you are having all these problems with your fan motor. There are several things that can cause a fan motor to go out prematurely. I will list some of them below then you can assess whether any of these might be causing your fan motor to go out so often. 1. Installing a universal fan motor that is not matched correctly with the right RPM or horsepower to power the fan blade. Motor not matched to the diameter and pitch of the fan blade. Motors should be matched (RPM, Horsepower, Amps) with the fan blades or it will over-load the motor and the motor will fail soon. 2. Having a fan blade that is off-balance and causes vibration to the motor and unit. A new balanced blade would be best. 3. Installing a fan motor and capacitor where the capacitor does not match the specs on the label of the fan motor. The fan motor capacitor should match the specifications on the motor label. 4. Installing a fan motor where lots of moisture is present like from a leaking gutter or down spout. Water pours on to fan motor when it rains or when snow melts. 5. Not having the rain shield installed (when required) or leaving drain plugs open where water and moisture can get into the motor. Some motors have rain shields to prevent water from getting into the motor. Many universal motors do not have rain shields, but have drain plugs that can be opened or closed depending on how the motor is installed, horizontal, vertical, shaft up or shaft down. 6. Improper wiring. Where the motor is not wired according to the label on the motor. 7. Improper rotation of the fan blade. With the fan blade spinning in the wrong direction the motor will not load and it will burn up over time. 7. Grass, weeds, plants or children that stick into the fan blade path and stop or impede the fan motor when it is running. More than likely the HVAC company you had installed a universal fan motor. Many of these motors use an individual capacitor and this is why they did not hook into your existing dual capacitor. They probably are using the dual capacitor for the compressor only and the fan motor they installed has a separate single capacitor. I am just guessing. I am thinking that probably number 1 is probably the problem. That is why we mostly sell OEM fan motors so they will be matched with the fan blade and the customer has an easy time with the installation. If you would send your unit’s model number I will try to find out which OEM motor fits your unit. Our support email address is: email@example.com. We will be glad to try and help you out! Steve Arnold
We sell furnace parts, air conditioning parts, AprilAire filters, EZ Flex filters, and many other HVAC parts and supplies at affordable prices. Place your order today! We would love to have your business!
Arnold’s Service Company, Inc. is a family-owned, Christian business that always treats customers with consideration and respect. If you are looking for an HVAC products supplier that will treat you the way you should be treated, turn to us. We carry a huge range of brand name items that can be purchased online. Whether you need furnace ignitors, AprilAire filters, EZ Flex filters, or another kind of HVAC merchandise, we want to serve you. We offer same-day shipping on most products, so you won’t have to do without the goods you need for long. If you ever experience a problem with any of your orders, contact us right away and we will make it right.