Purchase Your UHS24 ESP Universal Humidifier Water Solenoid Valve 24 Volts from Us and Save!
Same Business Day Shipping!
We Would Love to Help You Out and Have Your Business!
- The UHS24 ESP Universal Humidifier Water Solenoid Valve 24 Volts is brand new and comes in a sealed plastic covered ESP factory board.
- The UHS24 universal humidifier solenoid valve replaces many 24 volt humidifier solenoid valves on Aprilaire, General, Honeywell and Skuttle humidifiers.
- The UHS24 universal humidifier solenoid valve replaces Aprilaire 4040, General 990-53, Honeywell 32001639-002, Skuttle A01-0814-148.
- The UHS24 ESP Universal Humidifier Water Solenoid Valve 24 Volts replaces over 32 OEM humidifier solenoid valves.
- This universal solenoid valve is in stock and ready to ship.
- Same business day shipping if you order before 3 PM Eastern Time.
- Please email us anytime if you have a question. Our email address is: firstname.lastname@example.org.
- We have instructions below explaining how to replace a humidifier water solenoid valve.
- We would Love to help you out and have your business!
Solenoid Valve Replacement Instructions:
- For power units unplug electrical cord. For bypass units turn off power to furnace. Also turn the humidistat off.
- Shut off water supply at the saddle valve
- Disconnect inlet and outlet water compression nuts. Double wrench. Note, some water may drip on floor. Remove the orifice (which controls the water flow) from the plastic or copper tube and make sure there is no obstruction. If blocked clean or replace.
- Remove the wire nuts from the water solenoid valve wire connections. Set aside.
- Remove screws that secure valve to unit.
- Attach new valve with screws. Do not over-torque screws into plastic housing.
- Reconnect wires with wire nuts.
- For units with plastic feed tubes inspect for brittleness, hairline cracks, nicks or abrasions, etc. Replace if necessary.
- I would highly recommend completing this step while the humidifier water supply line is disconnected to clean out the supply line/saddle valve and make sure that you have a good flow of water coming out of the water supply line. Many times a new valve can become stopped up if this step is not completed. This can be accomplished by taking a bucket, setting the loose humidifier water supply line down into the bucket (two people are best), then turn on the saddle valve to get all loose sediment out of the saddle valve and the water line. This can be accomplished by allowing the water to run into the bucket for 10 to 15 seconds. If you can not get adequate water flow out of your saddle valve then you will need to replace your saddle valve. We sell a real good Supco saddle valve.
- Reconnect the water lines, double wrenching the compression nuts.
- Turn water back on and check system for leaks. Tighten compression nuts as necessary.
- Restore electrical service and activate furnace by turning up the thermostat.
- Turn up humidistat to verify operation of humidifier.
- Recheck for leaks. Turn down humidistat to make sure valve shuts off. Reset humidistat and thermostat to original levels.