Purchase the 626467 Nordyne Furnace Limit Switch from Us and Save!
This Limit Switch will be Shipped the Next Business Day. Order before 9 AM. Eastern Time for Same Day Shipping.
We Would Love to Help You Out and Have Your Business!
- The 626467 Nordyne Furnace Limit Switch is used on Gibson, Frigidaire, Philco, Tappan and other brand Nordyne gas furnaces and gas packs.
- This furnace limit has the part number 626467 and L200-20F on the front plate of the limit. The factory box has part #626467R on it.
- The 626467 furnace limit is set to break the circuit if the furnace heat exchanger reaches 200 degrees F.
- FYI: A furnace limit is a safety device that is used to cut the gas burners off if the furnace over-heats. If your furnace is going off on limit you might have an air flow problem like a dirty filter, dirty blower, slow blower motor (might need a new capacitor) stopped up evaportator coil or too much gas pressure. All of these can cause the furnace to over-heat and go off on limit. Many times when the furnace goes off on limit the fan blower will continuously blow because the furnace control board senses that the furnace has over-heated and needs to cool down. The only way to get the blower to cut off is to turn off the furnace with the power switch. You can test a limit with a volt meter to see if it is open or not. On most limits you should get 24 volts from each of the two wires on the limit to a good ground.
- Please email us anytime if you have a question. Our email address is: firstname.lastname@example.org
- We would Love to Help You Out and Have Your Business!