Question: I forgot how to wire up the dual round capacitor that I purchased from you. How do I go about wiring it up so it doesn’t blow the capacitor up again?
Answer: Thanks for your interest in our web site! You would need to look at the wiring diagram that came with the unit. Usually the wiring diagram is glued to one of the panels on the air conditioner. Hope you can read it. Rule of thumb on wiring the capacitor is: Herm on capacitor goes to the start winding on the compressor, Fan on capacitor goes to brown fan wire that goes to the fan, and Com on the capacitor comes off one leg of the contactor to provide power to the capacitor. There are usually more than one wire connected to the Com terminal. The Com terminal is used so other components of the air conditioner can steal power off the Com connection. We have a really good YouTube Video below that shows how to change and wire a capacitor on an air conditioning unit. I hope this post and video helps you out. We sell capacitors on the following page: Please click here if you would like to see some of the 60 or more different capacitors that we sell. If you have any questions please let us know. Our email is email@example.com
We would love to help you out and earn your business!